XT16 Room control
with power section with room
and „open window
This devices are designed for the selective heating of
defined areas and are not suitable as sole space hea-
Due to the nature of IR radiation (mainly medium wave)
effective for outdoor use in protected, semi-open areas
with low wind movement.
The minimum installation height is 1.8 m, the maximum instal-
lation height is 3.0 m depending on the model and application.
Despite the low enclosure temperature of max. 100 °C at the
rear of the housing, the mounting surface should be made
of non-flammable materials or, when mounting on flammable
surfaces (wooden beams), the „EXTENSION“ #7706 spacer
should be used.
For wall mounting, the distance to the ceiling must be at least
30 cm and the lateral distance to walls at least 50 cm.
ca. 6,5 m²
∆ T max.: + 6,5 °K
Data AAREN AAREN D with remote control
Code no. colour back 966V 966VD
Code no. colour white 966W 966WD
Heating area approx. (m²) 6,5 6,5
Heating-up time approx. (sec.) < 5 < 5
Minimum ceiling distance (cm) 9,5 9,5
Length L (mm) 800 1050
Weight approx. (kg) 5,3 7,1
Power (W) 1.800 1.800
Current approx. (A) 8,0 8,0
Voltage / Frequency (V / Hz) 220 - 240/~50/60 220 - 240/~50/60
Degree of prot. / protection class IP55 / I IP55 / I
Length of cable (m) 3,0 3,0
Material Aluminum/Schott NEXTREMA
The devices are designed for the selective
heating of defined areas and are not suitable
as sole space heating.
* For indoor use, the XT16 external con-
troller or equivalent must be used to
comply with the Ecodesign Regulation EU
2015/1188. This controller controls the use
of the device via a room thermostat, a week-
day control, an operating time limiter and an
„open window detection“.